|Name:||SCR Voltage Regulator Scr Thyristor Power Controller||Certificate:||ISO9001:2000，EU, UL,CUL,RoHS|
|Specification Model:||CTS-I-22KW CTS-I-28KW CTS-I-33KW||Rated Power:||22KW 28KW 33KW|
|Rated Current:||115A 146.3A 172.5A||Install Hole Spacing (mm):||204×127|
|Dimensions (L×W×H) (mm):||255×139×191||Fuse Specification (A):||140 16 200|
|Fuse Mounting Type:||Built In|
220v Scr Voltage Regulator,
4000w Scr Voltage Regulator,
40kw 220v Scr Voltage Regulator
SCR Voltage Regulator Scr Thyristor Power Controller
Description of SCR Voltage Regulator
Specification of SCR Voltage Regulator
CTS Series Single- phase Voltage Regulator
CTS for SCR single-phase AC voltage regulator, using national patent cooling duct and insulation terminals design. With compact structure and appearance, work instructions for clarity, convenient installation, wiring is simple, reliable work, etc.
◆Voltage regulating range: 0-220VAC or 0-380VAC continuous a djustable
◆Load type: single -phase electric heating load
◆Control mode: 1,Automatic mode: 4-20mA or 1-5VDC or 2-10VDC
2,Manual mode: 2.2 K-10K/2W potentiometer these are four modes for your choice
CTS voltage regulator adopt phase shift trigger type to achieve voltage adjust, in order to reach the purpose of the control voltage. The range of output voltage is generally rated voltage's 0-98%. With soft start, soft shut off, current limit and constant current and phase lack protection, load disconnection protection, over-current protection, overheating protection etc.
1,Soft start, soft turn off function: soft starter soft shutoff is refer to the power input use or voltage have change , the output will not subsequently change. In the perceptual load occasions, can prevent shock power and backward high-pressure impulse current of SCR damage. When the phased input, soft start and soft shut off can output gently change. Soft starter and soft shut off time for 2-8 seconds.
2,Overheating protection function: if the environmental temperature on the high side or the fan stop, radiator temperature may exceed 80℃, volatge regulator will quickly automatic stop all output, and slef-locking. At this time, must cut off power, check the fan can restarting work.
|CTS-type I Single- phase Regulator Selection, Installation Dimensions and Fuse Configuration|
|Specification model||Rated power||Rated current|
Install hole spacing